Today we were called out at High Point Medical in Cd’a for a clogged sewer line on a commercial building that multiple plumbing companies tried to unclog but were not successful. Upon diagnosis, we found the main backwater valve was clogged with frozen toilet paper and the valve was frozen shut. We tried to remove […]
About Admin Scott
This author has yet to write their bio.Meanwhile lets just say that we are proud Admin Scott contributed a whooping 13 entries.
Entries by Admin Scott
Today we performed leak detection on a house Newman Lake and found a leak inside the wall at the copper pipe connection on the shower valve. There was so much water damage that we have to perform water mitigation and then we will demo the old shower and install a beautiful brand new Koehler shower.
We installed a sewage ejector pump and underground plumbing in a basement for a basement bathroom addition we are doing.
We installed two new urinals at the Post Office in Post Falls. Thanks to our hard working Federal Employees for their enduring service!
Today we finished installing a Takagi tankless water heater in Coeur d’Alene, Idaho.
We were called out to a Post Falls home on the Spokane river that flooded because of improperly installed plumbing pipes. We diagnosed the problem as poor workmanship that caused the solder joint to fail. We also found piping that was installed incorrectly causing electrolysis, and upon close examination we found severe erosion of the […]
We went to a house in Coeur d’Alene, Idaho in the Landings subdivision that was flooded and we found that improperly installed plumbing was the cause of the flooding. We quickly replaced the faulty section and got our customers water back on within a couple hours.
We replaced a backflow valve at Maverik Gas Station in Couer d’Alene, Idaho and we will have the valve certified and inspected today by a city of Coeur d’ Alene inspector.
We got called to CrossFit in Coeur d’Alene because the building flooded with sewage. Somebody had removed all the parts on the backwater valve and when they got a clog, sewage flooded into building. This is a major health hazard! This is why only licensed plumbers should work on plumbing and why we only hire […]
This is a video of a home with severe sediment draining out of a water heater in Hayden, Idaho. The sediment ruined the previous water heater and it had to be replaced. A whole house filtration system can help prevent problems like this in your home form happening. Call us today at (208) 999-7788 or […]